On July 9, 2013, an outbreak of Legionnaires' disease (LD) was identified at Long-Term Care Facility A in central Ohio. This article describes the investigation of the outbreak and identification of the outbreak source, a cooling tower using an automated biocide delivery system. In total, 39 outbreak LD cases were identified; among these, six patients died. Water samples from a cooling tower were positive for Legionella pneumophila serogroup 1, reactive to monoclonal antibody 2, with matching sequence type to a patient isolate. An electronic control system turned off cooling tower pumps during low-demand periods, preventing delivery of disinfectant by a timed-release system, and leading to amplification of Legionella in the cooling tower. Guidelines for tower maintenance should address optimal disinfection when using automated systems.
|Number of pages||6|
|Journal||Journal of environmental health|
|Publication status||Published - 1 Dec 2015|